David Doyle Electrical Ltd contract including for the complete electrical installation for a new Theatre Recovery Suite, at the Bon Secours Hospital in Tralee Co. Kerry.
The Recovery Suite works were completed in a LIVE hospital environment, so particular attention was paid to Noise, Dust etc.
The new installation included Distribution, UPS, IPS, Medical Traunking, Emergency Lighting, LED IP65 Main Area Lighting, Data, Cardiac Call, Emergency Call, & Fire Alarm.
A new UPS / IPS system was supplied and installed to the Theatre Recovery as part of the electrical contract, for power supply to the essential equipment, at the 8 no. bed head medical trunking locations. The UPS /IPS shall be N+1 redundant system with the UPS and isolation transformers located in the plant room, and the dual IPS distribution boards located in the Recovery Suite.
2 No15KVA UPS system were supplied to BS EN50091 to be provided to support the relevant IPS systems. The UPS battery must be capable of supporting the load for 60 Minutes. The UPS and Battery will be installed in the plantroom. Batteries are to be mounted on an Open Rack adjacent to the UPS. The UPS system shall include:
Each IPS system shall be a fully independent stand alone Single Isolated Power System (SIPS).
To ensure absolute physical, electrical and electronic independence, “multi-channel” systems shall not be accepted. Each SIPS shall incorporate the following components:
Bon Secours Healthcare
Eamon Costello (Kerry)